FIREPROOF COATING FOR ELECTRICAL CABLES
UGAMCOAT 290908 is tested and certified for 2 hour rating by Government of India's National Test House Mumbai.
HSN CODE 32099020
Water base, intumescent, fire retardant, flexible and thin coating for cables and cable trays. Thin film coating approximately 800 microns provides reliable fire protection without causing premature ageing or overheating of cables. Halogen and asbestos free coating. Rating of electrical cables is not reduced. Escape routes and power supply can be used for longer time. Flame spread and insulation damages are delayed in case of prolonged exposure to fire. Minimizes smoke generation thereby permitting use in enclosed areas. Burning drips and burning cable fragment drops are minimized to greater extent. Coated surfaces will not catch fire or ignite or spread fire. Meets many stringent international fire standards. Best coating with the highest fire protection amongst the coatings of this class. Chemically converts nitrogen oxide and chlorine produced during burning of cables to foam and charring material thereby reducing the possibility of toxic gasses emission.
HOW IT WORKS:
It forms foam when temperature reaches 200 degrees Celsius. This foam is heat and fire resistant and almost non conductive. This keeps the surface away from heat and hence does not allow the surface to receive or conduct the heat in other areas. Also since this forms foam and a charred layer, it does not allow oxygen to reach to the surface over which it is applied. Hence it protects the surface from catching fire.
Areas should be cleaned, dried and made free from oil and dust. Surface temperature should be greater than 20 degrees C Stir the can properly. Observe the viscosity for brushing / airless spraying. Add soft water if required. Apply minimum two coats or as per requirement to achieve 800 microns dry film thickness. If smooth and decorative finish is required apply UGAM EPOXY TOP COAT (suitable for intumescent coating). No primer is required for this system if to be applied over cables. But if application is over metallic surfaces, UGAM ZINC RICH PRIMER should be applied.
1. Applied to cables in many depots of Hindustan Petroleum
2. Bharat Petroleum all over India
3. Also applied at ONGC offshore locations
4. Mahindra and Mahindra Ltd
5. Bharat Forge Ltd
6. Electro Orifab
7. Apollo Tyres Ltd and many more…
The technical specification is correct to the best of our knowledge and under test conditions and we do not accept any liability towards misuse and contents of it. Product must be tested for specific use prior to use.
For further details or any queries please do not hesitate to contact us.